|Submission Date||March 19, 2019|
University of Nebraska at Omaha
OP-5: Building Energy Consumption
|3.66 / 6.00||
Figures needed to determine total building energy consumption:
|Performance Year||Baseline Year|
|Grid-purchased electricity||186,637.55 MMBtu||177,853.85 MMBtu|
|Electricity from on-site renewables||0 MMBtu||0 MMBtu|
|District steam/hot water (sourced from offsite)||0 MMBtu||0 MMBtu|
|Energy from all other sources (e.g., natural gas, fuel oil, propane/LPG, district chilled water, coal/coke, biomass)||214,008.88 MMBtu||192,259.34 MMBtu|
|Total||400,646.43 MMBtu||370,113.19 MMBtu|
Start and end dates of the performance year and baseline year (or 3-year periods):
|Start Date||End Date|
|Performance Year||July 1, 2017||June 30, 2018|
|Baseline Year||July 1, 2010||June 30, 2013|
A brief description of when and why the building energy consumption baseline was adopted (e.g. in sustainability plans and policies or in the context of other reporting obligations):
Energy consumption baseline was taken from FY11-13. These years were chosen to give us a solid historical representation of average use based on reliable data.
Gross floor area of building space:
|Performance Year||Baseline Year|
|Gross floor area of building space||4,750,000 Gross Square Feet||3,856,559 Gross Square Feet|
Source-site ratio for grid-purchased electricity:
Total building energy consumption per unit of floor area:
|Performance Year||Baseline Year|
|Site energy||0.08 MMBtu / GSF||0.10 MMBtu / GSF|
|Source energy||0.17 MMBtu / GSF||0.19 MMBtu / GSF|
Percentage reduction in total building energy consumption (source energy) per unit of floor area from baseline:
Degree days, performance year (base 65 °F / 18 °C):
|Degree days (see help icon above)|
|Heating degree days||6,041 Degree-Days (°F)|
|Cooling degree days||1,544 Degree-Days (°F)|
Floor area of energy intensive space, performance year:
|Laboratory space||211,191 Square Feet|
|Healthcare space||0 Square Feet|
|Other energy intensive space|
EUI-adjusted floor area, performance year:
Building energy consumption (site energy) per unit of EUI-adjusted floor area per degree day, performance year:
Documentation (e.g. spreadsheet or utility records) to support the performance year energy consumption figures reported above:
A brief description of the institution's initiatives to shift individual attitudes and practices in regard to energy efficiency (e.g. outreach and education efforts):
The Sustainability website provides some tips in regards to energy efficiency and conservation.
A brief description of energy use standards and controls employed by the institution (e.g. building temperature standards, occupancy and vacancy sensors):
MV and UV- Thermostats are locked at 68-75 degrees. Interior lights in UV and MV clubhouses on motion sensors.
The temperature of the hot water that is used to heat the building is based on the outside air temperature...the colder it is, the hotter the water gets. Rather than allowing individuals to set their office, locker room, or space temperatures, they control it through their computer-based building controls in the ice plant. This computer allows them to schedule event temperatures and humidity levels in advance and once the event is over it reverts back to their low occupancy set points automatically. As for exterior lighting, photocells monitor light levels, and as needed, release lighting contactors to turn on or off the lights. The building had a contractor come in a teach the employees on how to run the ice plant at a more efficient rate. This will allow the ice chillers to run at a better capacity
A building temperature policy was adopted in May 2009 to conserve energy and make the best use of our resources. Occupancy sensors have been installed in all new construction and major renovations in the last 10 years or so. All but two buildings have lighting retrofits and lighting control systems in place. This includes timers, daylight harvesting, and occupancy sensors. Energy metering (electricity, gas, chilled water, and steam) was installed in all major buildings to monitor UNO's energy use. Unfortunately, many of these early meters failed. The early meters have been replaced with new technology and more reliable readings of energy use information for all major buildings. Vending machines have been slowly replaced by ones with motion sensors, lightless models, or LED-lit machines. This was largely done because other users demanded it and vendors made large-scale changes in machine selection.
A brief description of Light Emitting Diode (LED) lighting and other energy-efficient lighting strategies employed by the institution:
All interior fixtures at MV and UV are LED. All exterior fixtures at UV are LED. MV pole lights are LED and back entry lights are LED.
There are times that are controlled through the lighting system. This allows the use of lights, TVs, and other electronic devices to turn off when no one is in the building to turn them off. All restrooms, offices, and other small areas are controlled by motion detection lighting
LEDs have been installed in most of the major buildings on campus, to replace incandescent and fluorescent tubes. LED lighting has been used in classrooms and public access areas. LEDs have replaced HIDs in the parking structures, parking lots, and public sidewalks.
A brief description of passive solar heating, geothermal systems, and related strategies employed by the institution:
The Barn at Glacier Creek Preserve uses geothermal heating and cooling. (This is not individually metered, so we are unable to report any values)
A brief description of co-generation employed by the institution, e.g. combined heat and power (CHP):
A brief description of the institution's initiatives to replace energy-consuming appliances, equipment and systems with high efficiency alternatives (e.g. building re-commissioning or retrofit programs):
UV's HVAC has been replaced by new heat pumps and AC units, including the clubhouse. It now uses R410A freon which is better for the environment. Went from a seasonal energy efficiency rating of ~12 to a rating of 16.
This is an ongoing effort, driven by Facilities Management & Planning and encouraged by Procurement. New construction and renovations will incorporate lighting control systems to provide daylight harvesting, two-level lighting in offices, vacancy sensors in common areas such as classrooms and conference rooms. It is a practice - not a policy - to replace appliances, equipment, and systems with energy-efficient alternatives.
The website URL where information about the programs or initiatives is available:
Additional documentation to support the submission: