|Submission Date||Oct. 10, 2014|
University of Alberta
OP-T2-18: Energy Metering
Utility Services Manager
Facilities and Operations
Does the institution meter all energy consumption (electricity, natural gas, purchased steam, etc.) for at least one building?:
A brief description of the metering system:
North Campus buildings are metered for electricity, steam, chilled water and natural gas. Data from our major power meters (campus feeders, on-site generation, and utility plants) are available in real time to administrative staff; all other power meters are read manually via meter cards.
Following is more information on the types of meters used at the university:
Electricity: GE energy and demand meters.
Steam: Orifice plate with dual DP cells for extended turndown ratio.
Chilled Water: Rosemount Magflow meters.
Natural Gas: Diaphragm or rotary meters.
The percentage of building space with energy metering:
The website URL where information about the metering system is available:
The percentage given is 90% because, while on North Campus each building is metered at the building level, on other campuses there are some bulk meters. North Campus is approx. 90% of the building space at UAlberta.
The information presented here is self-reported. While AASHE staff review portions of all STARS reports and institutions are welcome to seek additional forms of review, the data in STARS reports are not verified by AASHE. If you believe any of this information is erroneous or inconsistent with credit criteria, please review the process for inquiring about the information reported by an institution and complete the Data Inquiry Form.